ASME A112.19.13-2007 pdf download.ELECTROHYDRAULIC WATER CLOSETS.
1 GENERAL 1.1 Scope This Standard establishes performance, electrical/elec- tronic conformance, temperature, life cycle, marking, and identification requirements for electrohydraulic water closets. The use of alternate materials or methods are permit- ted, provided the proposed material or method complies with the performance requirements and intent of this Standard. 1.2 Units of Measurement Values are stated in U.S. Customary units and the International System of Units (SI). The U.S. Customary units shall be considered as the standard. 1.3 Reference Standards The following documents form a part of this Standard to the extent specified herein. Unless otherwise indi- cated, the latest issue shall apply. ANSI Z124.4, Plastic Water Closet Bowls and Tanks Publisher: International Association of Plumbing and Mechanical Officials, 20001 East Walnut Drive South, Walnut, CA 91789 ASME A112.19.2M,Vitreous China Plumbing Fixtures ASME A112.19.6, Hydraulic Performance Require- ments for Water Closets and Urinals Publisher: The American Society of Mechanical Engi- neers, ASME Order Department, 22 Law Drive, Box 2300, Fairfield, NJ 07007 UL 62, Flexible Cord and Fixture Wire UL 157, Gaskets and Seals UL 244A-1994, Solid-State Controls for Appliances UL 746C, Polymeric Materials — Used in Electrical Equipment Evaluations UL 778, Motor Operated Water Pumps UL 796, Printed-Wiring Boards UL 817, Cord Sets and Power-Supply Cords UL 1585, Class 2 and Class 3 Transformers Publisher: Underwriters Laboratories Inc., 333 Pfingsten Road, Northbrook, IL 60062
1.4 Electrohydraulic Water Closet An electrohydraulic water closet is a siphonic or wash-down water closet as described in ASME A112.19.2M with a nonmechanical trap seal. The water closet incorporates electrical motor(s), pump(s), and controllers to facilitate the flushing action. In this Standard, the term water closet means an electrohydraulic water closet unless otherwise indicated. 2 REQUIREMENTS 2.1 General 2.1.1 Water Closet. The water closet shall conform to the requirements contained in ASME A112.19.2M or ANSI Z124.4, as appropriate. It shall also meet the requirements of ASME A112.19.6. 2.1.2 Electronic and Electrical Components. The electronic and electrical components utilized in the water closet shall comply with the appropriate Underwriters Laboratories (UL) standard or portions thereof as may be indicated in this Standard. 2.2 Pump System The pump systems of an electrohydraulic water closet shall be tested as a water pump in accordance with UL 778. The applicable sections of UL 778 for compli- ance are: (a) Construction, sections 1 through 8 and 10 through 28; (b) Performance, sections 29 through 35 and 37 through 47; (c) Manufacturing and Production Tests, sections 49 and 50; (d) Rating, section 51; (e) Markings, sections 48, 52, and 53; (f) Instruction, sections 54 and 55. 2.3 Pump Motor and Impeller The pump motor to the pump impeller coupling shall be nonmechanical and seamless.
2.4 Pump Housing Electric motors or pump enclosures shall comply with UL 746C and be plastic rated 94-5V or better as specified in UL 746C. 2.5 Jet Hose The pump jet hose, if provided, shall withstand a pressure of 25 ± 1 psi (172 ± 6.9 kPa) for 60 min. 2.6 Printed Wiring Boards Wiring boards shall comply with UL 244A-1994, sections 14.1 and 14.2, and UL 796. 2.7 Switches Switches shall be located in class 2 circuits only. NOTE: A class 2 circuit is a circuit with an open potential of no more than 30 V rms (42.2 V peak) supplied by either an inherently limited class 2 transformer or by a transformer and fixed impedance that together comply with all the requirements for inherently limited class 2 transformers in UL 1585. 2.8 Electrical Supply Cord Electrical supply cords shall be provided with 3 ft (0.9 m) minimum, 6 ft (1.8 m) maximum ofpermanently attached cord and an attachment plug for connection to the branch-circuit supply. The cord shall conform to UL 62 or UL 817. It shall be marked “Water Resistant” and include an equipment-grounding conduc- tor. Where the electrical supply cord exits the fixture, the surface shall be smooth, with rounded surfaces or provided with a grommet. Seals and gaskets shall conform to UL 157.